Air Curtain WING - Your Invisible Barrier
|Exchanger type||Ambient curtain (without exchanger)
|Range of heating power||-
|Maximum air efficiency||1950-4600 m3/h
|Maximum air range||4 m
The device is made with attention to detail, from high quality materials.
The refined housing design ensures stable and quiet operation of the device, guaranteeing comfort for room users.
High quality materials, unique shape and rigid construction are the basic assumptions of the designers of the curtain.
Simple cleaning of the curtain, double protective coating and efficient and durable EC motor ensure trouble-free operation of the device.
WING air curtains can be mounted horizontally or vertically*. Due to the slim design, very small height of the casing and the inclined air inlet, the device may be mounted in a limited space above the door, without any effect on performance.
* WING W, WING C
The width of the air outlet from the air curtain should be wider than or equal to the width of the door opening. In order to ensure effective protection, set the fan speed to such a level that regardless of the mounting height, the air speed near the floor is not less than 2 m/s.
The glands are located on the right side of the curtain behind the motor. The picture shows the placement of the cable grommets: no. 1 - grommet of the control cables, no. 2 - grommet of the supply lines, no. 3 - outlet grill of the motor.
|Type||L x W x H [mm]|
|WING 100||1157 x 520 x 310|
|WING 150||1675 x 520 x 310|
|WING 200||2194 x 520 x 31|
|Type||W1 [mm]||W2 [mm]|
For vertical mounting use screws M8x70. Screw 2 or 3 handles through the flat washers to the threaded sleeves mounted at the top section of the housing. Keep a minimum distance of 10 cm from the floor in order to provide access to the water drain nozzles from the heat exchanger and the terminal strip.
Yes, you can. The most frequently used non-freeze medium is a water solution of ethylene glycol. The heaters mounted in WING can support up to 50% mixtures. Make sure to check, however, if other elements of the technological heat installation (valves, pump, etc.) are adapted to work on glycol mix. To do this, check the recommendations of the manufacturers of particular components used. Remember that the use of glycol mixes, which are usually characterized by higher viscosity and lower thermal capacity, compared to water, increases the resistance of heating medium flow and reduces the heating power of the device.
The noise generated by the air curtain is the result of the fan impeller operation and expeditious flow of air within the device. The motor itself, regardless of the type , generates very little noise, which is incomparably quieter than the noise of the impeller. Therefore, regardless of the motor type the difference in the noise generated by the entire device will be indistinguishable by the human ear.
The reed switch offered by VTS will be able to serve air curtains with EC motors only. There is a possibility to connect one reed switch to one controller WING EC. Controller can control up to 8 air curtains WING EC.
Yes, it is possible to mount the curtains in groups, which enables the security of the door opening of any length (eg. 3 m, 3.5 m, 4 m, etc.).
All devices, regardless of the length, are designed to be installed both ways: horizontally (WING W/E/C) and vertically (WING W/C). In the case of vertical installation it is possible to mount the motor pointing upwards or downwards. The mounting method does not affect system stability in any way. Please note that the air curtains with electrical heaters (WING E100-E200) are not suitable for vertical mounting.
Due to the contact load, the wall-mounted WING controller can be used to supply only one WING curtain. In order to control more curtains with a single controller, use an additional contactor in the power supply circuit of the curtains. For more detailed information, please consult VTS technical support department.
When connecting a door sensor it is not recommended to use a valve with an actuator due to increased inertia of the system i.e. the heating time of the heat exchanger and the time it takes for the actuator to open the valve.
Yes. The controller Wing EC allows adjustment of heating power of the WING E. For WING W equipped with a valve it is possible to enable or disable function of heating. Without a valve, the heat exchanger remains in the free flow of the heating agent.
The air temperature prevailing in the room or the temperature
to be set and maintained by other heating systems.
WING ambient curtains are air curtains without any function of air heating. Such curtains are not equipped with a water or electric heater. From the user’s point of view this means that the temperature of the air stream at the curtain’s outlet is equal to the temperature of the air drawn from the environment.
The WING air curtain is not suitable for installation in suspended ceilings, as this could restrict the air flow in front of the individual components. The minimum distance that must be maintained between the device and the ceiling is 10 cm.